# Wire Size Calculator

Calculate the minimum size of a wire or conductor needed for a circuit, or calculate the dimensions of the wire, including the diameter, cross-sectional area, and resistance given its gauge.

%

## Minimum Wire Size:

AWG

### Expected Voltage Drop

%
Learn how we calculated this below

## How to Calculate Wire Size

A wire gauge is a standard unit for measuring the diameter of the wire, and American Wire Gauge (AWG) is the standard used in North America for conductors in electrical systems. Depending on the application, it is essential to use conductors of the proper size for safe and reliable power delivery and to reduce the amount of voltage drop in the system.

An oversized conductor could be a waste of money, and an undersized conductor might not be able to handle the required current flows, which is why choosing the correct wire size is so important.

### Minimum Wire Size Formula for Single-Phase Circuits

Use the following formula to calculate the minimum wire size for a DC or single-phase AC circuit:[1]

A(m²) = 2 × ρ(Ω·m) × L(m) × I(A) / V(V)

Where:
A = cross-sectional area in square meters
ρ = conductor resistivity in ohm-meters (Ω·m)
L = length in meters
I = current in amps
V = allowable voltage drop in volts

Thus, the minimum cross-sectional area A for a wire in square meters is equal to the product of two, the conductor resistivity ρ, its length L in meters, and the current I in amps, divided by the allowable voltage drop V in volts.

The resistivity of a copper conductor is 1.7241×10-8 Ω·m and the resistivity of an aluminum conductor is 2.6548×10-8 Ω·m.

To convert the resulting cross-sectional area to square millimeters, multiply the result by 1,000,000.

A(mm²) = (m²) × 1,000,000

For example, let’s calculate the wire size of a 100-meter-long copper wire for a single-phase circuit when it must supply 30 amps of current with a 10 V voltage drop allowed:

A(mm²) = 2 × 1.7241×10-8 Ω·m × 100 m × 30 A / 10 V × 1,000,000
A(mm²) = 10.3446×10-6 m² × 1,000,000
A(mm²) = 10.3446 mm²

By comparing the size to the list of AWG wire sizes in the chart below, we can see that a 7 AWG wire size, which has a cross-sectional area of 10.549 mm², will meet the minimum requirements for this circuit.

Note that these formulas do not account for temperature variation or any national or local electric codes, such as the National Electric Code, that might require a larger gauge conductor, depending on the application.[2] You can use our wire ampacity calculator to confirm the conductor supports the current requirements for the application.

Always consult a qualified electrical professional before installing or altering electrical wiring or components.

### Minimum Wire Size Formula for Three-Phase Circuits

The formula to calculate the wire size for a three-phase AC circuit is slightly different:

A(m²) = √3 × ρ(Ω·m) × L(m) × I(A) / V(V)

The minimum cross-sectional area A for a wire in square meters is equal to the product of the square root of three, the conductor resistivity ρ, its length L in meters, and the current I in amps, divided by the allowable voltage drop V in volts.

Solving the same example as before, but for a three-phase circuit, we get:

A(mm²) = √3 × 1.7241×10-8 Ω·m × 100 m × 30 A / 10 V × 1,000,000
A(mm²) = 8.9586×10-6 m² × 1,000,000
A(mm²) = 8.9586 mm²

By comparing the size to the list of AWG wires, we can see that a 7 AWG wire size will still meet the minimum requirements for this circuit.

To find the gauge of wire required, use the chart below to find the wire gauge with the necessary cross-sectional area.

## How to Calculate a Wire’s Area and Diameter

You can calculate the wire size, diameter, and cross-sectional area using the wire gauge and a few simple formulas.

### Wire Diameter Formula

The formula to find the diameter of the wire in inches is:

D(in) = 0.005 × 92(36 – AWG) ÷ 39

The formula to find the diameter of the wire in millimeters is:

D(mm) = 0.127 × 92(36 – AWG) ÷ 39

#### Steps to Find the Diameter of a Conductor

First – find the exponent in the equation by subtracting the wire gauge from 36 and then dividing by 39.

Finding the exponent for 00, 000, and 0000 gauge wire is slightly different. Substitute -1, -2, and -3 for the gauge in the formula above instead of the AWG value.

Second – find 92 to the power calculated in the previous step.

Third – multiply the value from the second step by either .005 inches or .127 mm to find the diameter of the wire in inches or millimeters, respectively.

### Wire Cross-Sectional Area Formula

The formula to find the cross-sectional area of the wire in kilo-circular mils, or kcmil, is:

A(kcmil) = 1,000 × D(in)²

The formula to find the cross-sectional area of the wire in square millimeters is:

A(mm²) = π / 4 × D(mm)²

#### Steps to Find the Cross-Sectional Area of a Conductor

First – find the diameter of the wire. Use the formula above to calculate the width if the AWG is known.

Second – multiply the diameter by 1,000 to find the area in kcmil or by (3.1415 ÷ 4) to calculate square millimeters.

## Wire Gauge Chart

Chart showing the wire size, diameter, cross-sectional area, and resistances for conductors of each gauge. Resistance values assume a copper conductor at 20 °C (68 °F) with a resistivity of 1.7241×10-8 Ω·m.
AWG Diameter Cross-Sectional Area Resistance
(inches) (mm) (kcmil) (mm²) Ohms per 1,000 ft Ohms per 1,000 m
0000 (4/0) 0.46 11.684 211.6 107.22 0.049 0.1608
000 (3/0) 0.4096 10.405 167.81 85.029 0.0618 0.2028
00 (2/0) 0.3648 9.266 133.08 67.431 0.0779 0.2557
0 (1/0) 0.3249 8.251 105.53 53.475 0.0983 0.3224
1 0.2893 7.348 83.693 42.408 0.1239 0.4066
2 0.2576 6.544 66.371 33.631 0.1563 0.5127
3 0.2294 5.827 52.635 26.67 0.197 0.6464
4 0.2043 5.189 41.741 21.151 0.2485 0.8152
5 0.1819 4.621 33.102 16.773 0.3133 1.028
6 0.162 4.115 26.251 13.302 0.3951 1.296
7 0.1443 3.665 20.818 10.549 0.4982 1.634
8 0.1285 3.264 16.51 8.366 0.6282 2.061
9 0.1144 2.906 13.093 6.634 0.7921 2.599
10 0.1019 2.588 10.383 5.261 0.9988 3.277
11 0.0907 2.305 8.234 4.172 1.26 4.132
12 0.0808 2.053 6.53 3.309 1.588 5.211
13 0.072 1.828 5.178 2.624 2.003 6.571
14 0.0641 1.628 4.107 2.081 2.525 8.285
15 0.0571 1.45 3.257 1.65 3.184 10.448
16 0.0508 1.291 2.583 1.309 4.015 13.174
17 0.0453 1.15 2.048 1.038 5.063 16.612
18 0.0403 1.024 1.624 0.823 6.385 20.948
19 0.0359 0.9116 1.288 0.6527 8.051 26.415
20 0.032 0.8118 1.022 0.5176 10.152 33.308
21 0.0285 0.7229 0.8101 0.4105 12.802 42.001
22 0.0253 0.6438 0.6424 0.3255 16.143 52.962
23 0.0226 0.5733 0.5095 0.2582 20.356 66.784
24 0.0201 0.5106 0.404 0.2047 25.668 84.213
25 0.0179 0.4547 0.3204 0.1624 32.367 106.19
26 0.0159 0.4049 0.2541 0.1288 40.814 133.9
27 0.0142 0.3606 0.2015 0.1021 51.466 168.85
28 0.0126 0.3211 0.1598 0.081 64.897 212.92
29 0.0113 0.2859 0.1267 0.0642 81.833 268.48
30 0.01 0.2546 0.1005 0.0509 103.19 338.55
31 0.008928 0.2268 0.0797 0.0404 130.12 426.9
32 0.00795 0.2019 0.0632 0.032 164.08 538.32
33 0.00708 0.1798 0.0501 0.0254 206.9 678.8
34 0.006305 0.1601 0.0398 0.0201 260.9 855.96
35 0.005615 0.1426 0.0315 0.016 328.98 1,079.3
36 0.005 0.127 0.025 0.0127 414.84 1,361
37 0.004453 0.1131 0.0198 0.01 523.1 1,716.2
38 0.003965 0.1007 0.0157 0.007967 659.62 2,164.1
39 0.003531 0.0897 0.0125 0.006318 831.77 2,728.9
40 0.003145 0.0799 0.009888 0.00501 1,048.8 3,441.1

Also, see our electricity cost calculator or our lighting cost calculator before you plan your next electrical project.

## References

1. Miller, C., NFPA's Electrical References, National Fire Protection Association, 2004, Jones & Bartlett Learning, 235-238. https://www.google.com/books/edition/NFPA_s_Electrical_References/raUyIi7i-asC
2. Vigstol, D., Determining Current Carrying Capacity of Conductors, National Fire Protection Association, July 21, 2021, https://www.nfpa.org/News-and-Research/Publications-and-media/Blogs-Landing-Page/NFPA-Today/Blog-Posts/2021/07/21/Determining-Current-Carrying-Capacity-of-Conductors