# Wire Size Calculator

Calculate the minimum size of a wire or conductor needed for a circuit, or calculate the dimensions of the wire, including the diameter, cross-sectional area, and resistance given its gauge.

## Minimum Wire Size:

### Expected Voltage Drop

inches: | |

millimeters: |

### Cross-sectional Area

kcmil: | |

square inches: | |

square millimeters: |

### Cross-sectional Area

kcmil: | |

square inches: | |

square millimeters: |

## On this page:

## How to Calculate Wire Size

A wire gauge is a standard unit for measuring the diameter of the wire, and American Wire Gauge (AWG) is the standard used in North America for conductors in electrical systems. It is essential to use conductors of the proper size for safe and reliable power delivery, and to reduce the amount of voltage drop in the system.

### Minimum Wire Size Formula for Single-Phase Circuits

Use the following formula to calculate the minimum wire size for a DC or single-phase AC circuit:^{[1]}

A_{(mm²)} = 2 × ρ × L_{(m)} × I_{(A)} / V_{(V)}

Where:

*A* = cross-sectional area in square millimeters

*ρ* = conductor resistivity in ohm-meters (Ω·m)

*L* = length in meters

*I* = current in amps

*V* = allowable voltage drop in volts

Thus, the minimum cross-sectional area *A* for a wire in square millimeters is equal to the product of two, the conductor resistivity *ρ*, its length *L* in meters, and the current *I* in amps, divided by the allowable voltage drop *V* in volts.

The resistivity of a copper conductor is 1.7241 × 10^{-8} Ω·m and the resistivity of an aluminum conductor is 2.6548 × 10^{-8} Ω·m.

### Minimum Wire Size Formula for Three-Phase Circuits

The formula to calculate the wire size for a three-phase AC circuit is slightly different:

A_{(mm²)} = √3 × ρ × L_{(m)} × I_{(A)} / V_{(V)}

The minimum cross-sectional area *A* for a wire in square meters is equal to the product of the square root of three, the conductor resistivity *ρ*, its length *L* in meters, and the current *I* in amps, divided by the allowable voltage drop *V* in volts.

To find the gauge of wire required, use the chart below to find the wire gauge with the necessary cross-sectional area.

## How to Calculate a Wire’s Area and Diameter

You can calculate the wire size, diameter, and cross-sectional area using the wire gauge and a few simple formulas.

### Wire Diameter Formula

The formula to find the diameter of the wire in inches is:

D_{(in)} = .005 × 92^{(36 – AWG) ÷ 39}

The formula to find the diameter of the wire in millimeters is:

D_{(mm)} = .127 × 92^{(36 – AWG) ÷ 39}

#### Steps to Find the Diameter of a Conductor

**First** – find the exponent in the equation by subtracting the wire gauge from 36 and then dividing by 39.

Finding the exponent for 00, 000, and 0000 gauge wire is slightly different. Substitute -1, -2, and -3 for the gauge in the formula above instead of the AWG value.

**Second** – find 92 to the power calculated in the previous step.

**Third** – multiply the value from the second step by either .005 inches or .127 mm to find the diameter of the wire in inches or millimeters, respectively.

### Wire Cross-Sectional Area Formula

The formula to find the cross-sectional area of the wire in kilo-circular mils, or kcmil, is:

A_{(kcmil)} = 1000 × D_{(in)}²

The formula to find the cross-sectional area of the wire in square millimeters is:

A_{(mm²)} = π / 4 × D_{(mm)}²

#### Steps to Find the Cross-Sectional Area of a Conductor

**First** – find the diameter of the wire. Use the formula above to calculate the width if the AWG is known.

**Second** – multiply the diameter by 1000 to find the area in kcmil or by (3.1415 ÷ 4) to calculate square millimeters.

## Wire Gauge Chart

AWG | Diameter | Cross-Sectional Area | Resistance | |||
---|---|---|---|---|---|---|

(inches) | (mm) | (kcmil) | (mm²) | Ohms per 1000ft | Ohms per 1000m | |

0000 (4/0) | 0.46 | 11.684 | 211.6 | 107.22 | 0.049 | 0.1608 |

000 (3/0) | 0.4096 | 10.405 | 167.81 | 85.029 | 0.0618 | 0.2028 |

00 (2/0) | 0.3648 | 9.266 | 133.08 | 67.431 | 0.0779 | 0.2557 |

0 (1/0) | 0.3249 | 8.251 | 105.53 | 53.475 | 0.0983 | 0.3224 |

1 | 0.2893 | 7.348 | 83.693 | 42.408 | 0.1239 | 0.4066 |

2 | 0.2576 | 6.544 | 66.371 | 33.631 | 0.1563 | 0.5127 |

3 | 0.2294 | 5.827 | 52.635 | 26.67 | 0.197 | 0.6464 |

4 | 0.2043 | 5.189 | 41.741 | 21.151 | 0.2485 | 0.8152 |

5 | 0.1819 | 4.621 | 33.102 | 16.773 | 0.3133 | 1.028 |

6 | 0.162 | 4.115 | 26.251 | 13.302 | 0.3951 | 1.296 |

7 | 0.1443 | 3.665 | 20.818 | 10.549 | 0.4982 | 1.634 |

8 | 0.1285 | 3.264 | 16.51 | 8.366 | 0.6282 | 2.061 |

9 | 0.1144 | 2.906 | 13.093 | 6.634 | 0.7921 | 2.599 |

10 | 0.1019 | 2.588 | 10.383 | 5.261 | 0.9988 | 3.277 |

11 | 0.0907 | 2.305 | 8.234 | 4.172 | 1.26 | 4.132 |

12 | 0.0808 | 2.053 | 6.53 | 3.309 | 1.588 | 5.211 |

13 | 0.072 | 1.828 | 5.178 | 2.624 | 2.003 | 6.571 |

14 | 0.0641 | 1.628 | 4.107 | 2.081 | 2.525 | 8.285 |

15 | 0.0571 | 1.45 | 3.257 | 1.65 | 3.184 | 10.448 |

16 | 0.0508 | 1.291 | 2.583 | 1.309 | 4.015 | 13.174 |

17 | 0.0453 | 1.15 | 2.048 | 1.038 | 5.063 | 16.612 |

18 | 0.0403 | 1.024 | 1.624 | 0.823 | 6.385 | 20.948 |

19 | 0.0359 | 0.9116 | 1.288 | 0.6527 | 8.051 | 26.415 |

20 | 0.032 | 0.8118 | 1.022 | 0.5176 | 10.152 | 33.308 |

21 | 0.0285 | 0.7229 | 0.8101 | 0.4105 | 12.802 | 42.001 |

22 | 0.0253 | 0.6438 | 0.6424 | 0.3255 | 16.143 | 52.962 |

23 | 0.0226 | 0.5733 | 0.5095 | 0.2582 | 20.356 | 66.784 |

24 | 0.0201 | 0.5106 | 0.404 | 0.2047 | 25.668 | 84.213 |

25 | 0.0179 | 0.4547 | 0.3204 | 0.1624 | 32.367 | 106.19 |

26 | 0.0159 | 0.4049 | 0.2541 | 0.1288 | 40.814 | 133.9 |

27 | 0.0142 | 0.3606 | 0.2015 | 0.1021 | 51.466 | 168.85 |

28 | 0.0126 | 0.3211 | 0.1598 | 0.081 | 64.897 | 212.92 |

29 | 0.0113 | 0.2859 | 0.1267 | 0.0642 | 81.833 | 268.48 |

30 | 0.01 | 0.2546 | 0.1005 | 0.0509 | 103.19 | 338.55 |

31 | 0.008928 | 0.2268 | 0.0797 | 0.0404 | 130.12 | 426.9 |

32 | 0.00795 | 0.2019 | 0.0632 | 0.032 | 164.08 | 538.32 |

33 | 0.00708 | 0.1798 | 0.0501 | 0.0254 | 206.9 | 678.8 |

34 | 0.006305 | 0.1601 | 0.0398 | 0.0201 | 260.9 | 855.96 |

35 | 0.005615 | 0.1426 | 0.0315 | 0.016 | 328.98 | 1,079.3 |

36 | 0.005 | 0.127 | 0.025 | 0.0127 | 414.84 | 1,361 |

37 | 0.004453 | 0.1131 | 0.0198 | 0.01 | 523.1 | 1,716.2 |

38 | 0.003965 | 0.1007 | 0.0157 | 0.007967 | 659.62 | 2,164.1 |

39 | 0.003531 | 0.0897 | 0.0125 | 0.006318 | 831.77 | 2,728.9 |

40 | 0.003145 | 0.0799 | 0.009888 | 0.00501 | 1,048.8 | 3,441.1 |

Also, see our electricity cost calculator or our lighting cost calculator before you plan your next electrical project.

## References

- Miller, C., NFPA's Electrical References,
*National Fire Protection Association*, 2004, Jones & Bartlett Learning, 235-238. https://www.google.com/books/edition/NFPA_s_Electrical_References/raUyIi7i-asC